Since the first examination in 2015, it is a set of test papers that candidates must do before the examination every year.
four In the high-rise ward building, refuge rooms shall be set in the ward floor on the second floor and above and the clean operation Department.
two When the inpatient part of the hospital and sanatorium adopts class III fire resistance rating buildings, it shall not exceed 2 floors; When a building with class IV fire resistance rating is adopted, it shall be single-layer; When it is set in a building with class III fire resistance rating, it shall be arranged on the first or second floor; When it is set in a building with class IV fire resistance rating, it shall be arranged on the first floor.
One evacuation door can be set in the room between two emergency exits or on both sides of the bag walkway in the medical building.
five The ward set in the civil air defense project shall be divided into independent fire compartments, and the evacuation stairs shall not be shared with the evacuation stairs of other fire compartments.
In case of difficulties, local application system can also be set.
2、 Safe evacuation 1 A single storey public building with a medical building area of no more than 200 m2 and a population of no more than 50 people can be provided with one emergency exit.
4、 Decoration materials v.
three The adjacent nursing units in the ward building of the hospital and sanatorium shall be separated by a fire partition wall with a fire resistance limit of not less than 2.00h.
six For the civil air defense project of a hospital with a building area of more than 500 m2, when the height difference between the indoor ground on the ground floor and the floor at the entrance and exit of the room is greater than 10m, a smoke proof staircase shall be set; When there are two floors underground and the height difference between the indoor ground of the second floor underground and the floor at the entrance and exit of the room is no more than 10m, a closed staircase shall be set.
three The minimum horizontal illumination of evacuation lighting on the ground of refuge room, staircase, front room or shared front room and refuge walkway in ward building or operation department shall not be less than 10.0lx.
four In civil air defense engineering, hospitals and with a building area of more than 100 ㎡ and less than or equal to 1000 ㎡ should be equipped with automatic sprinkler system.
3、 Fire fighting facilities 1 Wards and treatment areas of hospitals and sanatoriums, and collective activity places for the elderly, children and the disabled; Quick response sprinkler heads should be used.
three The net width of the first floor evacuation door and the first floor evacuation outer door of the staircase of high-rise medical building shall not be less than 1.30M, the net width of the walkway of the single-sided cloth room shall not be less than 1.40M, the net width of the walkway of the double-sided cloth room shall not be less than 1.50M, and the net width of the evacuation staircase shall not be less than 1.30M.
I believe this set of test papers can point out the direction for everyone to prepare for the test! In order to ensure that examinees can better understand the simulation prediction volume, Xuechuan teaching and Research Office will record high-definition explanation video courses of corresponding subjects (cost 199 yuan / subject).
You can scan the QR code on the back of the test paper.
When quick response sprinkler heads are used, the system shall be wet.
three Exhibition, store, catering and hotel buildings with a floor area of more than 1500 m2 or a total floor area of more than 3000 m2, as well as ward building, outpatient building and operation Department with the same building scale in the hospital; Unless otherwise specified in this specification and places not suitable for water protection or fire extinguishing, the following single and multi-storey civil buildings or places shall be equipped with automatic fire extinguishing system, and automatic sprinkler system should be adopted.
1、 Plane layout 1 The inpatient parts of hospitals and nursing homes shall not be set underground or semi underground.
When it is set on the first floor, the height difference between the indoor ground and the floor at the entrance and exit of the room shall not be greater than 10m.
In addition, the electronic version of “pre exam secret script” is attached.
The doors and windows that must be set on the wall shall be class B fire doors and windows.
four The hospital ward set in the civil air defense project shall not be set on the second floor and below the basement.
five For the evacuation stairs of multi-storey medical buildings, except the staircase directly connected to the open corridor, the closed staircase shall be adopted.
others 1 If hospitals, supermarkets, entertainment places and other densely populated places need to control the random access of personnel, such as emergency exits, evacuation doors, or access control systems, they shall ensure that they can be easily opened from the inside without using any tools such as keys in case of fire, and “emergency exits” signs and use tips shall be set at prominent positions.
two Automatic fire alarm system shall be set in the ward building of sanatorium with a building area of more than 1500 M2 on any floor or a total building area of more than 3000 m2, and the buildings or places such as hospital outpatient building, ward building and operation Department with no less than 200 beds.
two The continuous power supply time of standby power supply of medical building system shall not be less than 1.0h.
two The number of evacuation doors in each room in the medical building shall be determined by calculation and shall not be less than 2.
The door on the partition wall shall be class B fire door, and the fire door set on the walkway shall be normally open fire door.
Here comes the pre exam simulation prediction paper! The simulated prediction volume before the examination of registered fire engineer, which is most similar to the real problem, is selling well! The pre examination simulation forecast prepared by Xuechuan teaching and Research Office has been highly praised by the majority of candidates since its listing.
six The operating room or operating department, delivery room, intensive care unit, room for valuable and precision medical equipment, storage room, laboratory, film room, etc.
Through the continuous research and exploration of the real questions, the new version of the pre-test simulation prediction volume in 2021 can better grasp the law and trend of the proposition; Combined with the test outline and the new textbook of 2021, we have made accurate predictions for some test sites.
in the medical building, children’s activity places and elderly care facilities such as nursery, children’s room in kindergarten and children’s amusement hall attached to the building, The fire partition wall with fire resistance of not less than 2.00h and the floor slab with fire resistance of 1.00h shall be used to separate from other places or parts.